Wells Fargo has announced that it is exiting its lease at the Philadelphia Plaza building at 101 N. Independence Mall, leaving its office and data center and relocating to offices in Two Logan Square and Commerce Square.According to the company, no layoffs are set to take place, and there will...
Company: Agile Data Sites
Country: United States
Region: North America
Gross SqFt: 5,000
AGILE Allentown has a double-ended 110kV substation on premises, fed by PPL. In twelve years of operation, this campus has never lost power. The 110kV substation feeds a double-ended 12.5kV switchgear which in turn feeds the 480V output substation for the data center.
The data center power distribution features N+N redundant components with PLC-controlled switchboard feeding dual generators and a N+N uninterruptible power supply (UPS) system.
The HVAC system is made up of N+1 redundant air-cooled chillers with economization systems which feed in-row CRAH units. All CRAH units can be fed by either A or B power.
All critical systems are monitored by Tridium Niagara monitoring systems.